New double height entrance space including a new entrance screen, circular revolving automatic door and DDA compliant accessible pass door.
Simple palette of materials applied to the new entrance area which includes a bronzed effect anodized aluminium mesh panel wall which contrasts with the 6m high concrete panel wall and concrete reception desk.
Dedicated touch down seating area with four comfortable lounge seats and a low table, also included within this area is a high level working bench for 6 people with integrated power, data and WiFi.
New feature lighting design including 3 large format barrisol lighting rafts.
New glass wing slimline speed lanes creating a secure line before the lifts and main stair central core.
Balustrading refurbished to ensure fully compliant with current regulations.
New floor signage on each floor.
Carpet tile to stair treads and half landings to all levels.
Full height flush cubicle system.
All steelwork to the staircase painted.
Perforated suspended ceiling SAS system 330 generally, system 150 to stair and toilet lobbies throughout with plasterboard margins.
Medium grade raised access floor tiles with a 160mm void.
All doors spray lacquered white with satin stainless steel ironmongery.
All existing walls and skirting painted to match new works.
3 ‘knock out panels’ to the structural slab to allow future provision of interconnecting stairs between floor plates.
Full strip out of all fixtures and fittings, sanitary ware, wall linings etc.
Ceramic tiling to floor and walls with matching tiled skirting.
Feature wash trough with integrated vanity shelf and under counter waste bin.
Full height flush cubicle system.
Integrated towel dispensers and provision for wall mounted hand driers.
Plasterboard ceiling with in set and plain metal ceiling tiles for access to services.
New passenger lifts with lift car finishes, controls, doors, architraves and thresholds.
Controls to allow floor by floor access controllability as required.
1 no. 13 person/1000kg passenger lift operating at 1.6m/s in entrance core serving levels: Basement (-2), Lower Ground, Ground, 1, 2, 3, 4 & 5 with access control interface and 60 minute rated doors.
2 no. 13 person/1000kg passenger lifts operating at 1.6m/s in entrance core serving levels: Lower Ground, Ground, 1, 2, 3, 4 & 5 with access control interface and 60 minute rated doors.
New fully fitted male and female shower rooms with changing areas and lockers and separate DDA compliant toilet and shower.
External design condition: 25°C dry bulb/18°C wet bulb summer, -5°C dry bulb winter.
Internal office area design temperatures: 21°C winter/24°C summer.
Controls tolerance: ± 2°C.
Occupancy level: 1 person per 8m2 net office area for cooling and fresh air ventilation.
Fresh air supply rate: 12 litres per person.
Toilet extract ventilation rate: 10 air changes per hour extract.
Office lighting design load – 12W/m2.
Office small power design load – 25W/m2.
Office lighting level – 400 lux maintained illuminance at 0.75m working plane.
VRF, heat recovery, fan coil unit system providing comfort heating and cooling via ceiling void mounted units distributed in line with BCO Guide to Specification to provide flexibility for future cellularisation by tenants.
Mechanical fresh air supply and extract system with central air handling plant at roof level incorporating heat recovery.
Fan coil unit system provided with central time controls on a ¼ floor-by-floor basis with individual controllers to adjust each fan coil unit temperature set point.
Air handling plant coils and fan coil units served via external heat pumps located on the roof.
Mechanical extract ventilation to serve the toilet cores.
Decorative electric panel heating within staircases and basement areas.
Integrated Building Management System to serve the mechanical plant.
Main LV switchboard incorporating spare capacity and power factor correction equipment.
Lighting installation throughout the office area using recessed modular high frequency luminaires and downlighters in line with the design intent of CIBSE LG7 with occupancy detection and perimeter daylight dimming controls.
Lighting installation throughout the areas using a combination of high frequency functional and decorative luminaires with manual and occupancy detection control to suit the location.
General purpose socket outlets in landlord’s core areas and entrances.
Analogue addressable fire alarm system in accordance with BS 5839 Part 1 Category L1 with double knock operational capability.
Emergency lighting installation in accordance with BS 5266.
Dedicated tenant’s vertical IT cable containment.
Existing lighting protection system modified to suit refurbishment scheme.
CCTV installation serving external areas for landlord’s use.
Access control system to interface with passenger lifts.
Disabled refuge emergency voice communication system.
Public Health Services
Existing incoming mains water supply and recently refurbished cold water storage system retained. Storage tank and booster set located within lower ground floor.
Domestic hot water service served via localised electric water heating within each toilet area.
Water and drainage connections provided for future tenant’s tea point facilities.